Title: Electric cables for photovoltaic systems
Introduction to BS EN 50618
The BS EN 50618 standard covers low smoke halogen-free, flexible, single-core power cables with crosslinked insulation and sheath. They are intended for use on the direct current (d.c.) side of photovoltaic systems, with a nominal d.c. voltage of 1.5 kV between conductors and between conductor and earth.
The cables are suitable to be used with Class II equipment.
The cables are designed to operate at a normal maximum conductor temperature of 90 °C but for a maximum of 20,000 hours max. conductor temperature of 120 °C at a max. ambient temperature of 90 °C is permitted.
These cables are designed to be suitable for permanent outdoor use for many years under variable demanding climate conditions. Relatively stringent requirements are set in this standard, for these products, in line with the expected harsh usage conditions.
NOTE The expected period of use under normal usage conditions as specified in this standard is at least 25 years.
The cables specified in the BS EN 50618 standard are, in particular, designed for use at the direct current (d.c.) side of photovoltaic systems, with a nominal d.c. voltage of 1.5 kV between conductors as well as between conductor and earth. The maximum permitted operating d.c. voltage of the systems in which the cables specified in this standard are applied shall not exceed 1,8 kV.
The cables have a rated voltage of 1,0/1,0 kV when used in alternating current (a.c.) systems.
Annex A of the BS EN 50618 standard gives additional guidance on voltage ratings.
- The standard specifies the use of tin coated class 5 copper conductors and in accordance with EN 60228.
- The insulation and sheathing materials specified are cross-linked, full details of which are given in Annex B.
- The insulation and sheath are to be applied by extrusion.
NOTE: Insulation applied in more than one layer does not conform to the definition of “Double insulation” given, for instance, in HD 60364.
The standard designates these cables with the following core ‘H1Z2Z2-K’.
The size range included in the standard is 1,5 mm2upto and including 240 mm2
Table A.3 of the standard gives current carrying capacity for these PV cables
Related Case Studies
Tratos participates in the 28th Central Asian International Mining Exhibition
Queensland Government Delegation Visits Tratos Manufacturing Facility in Knowsley
Tratos hosted the first OPG showroom
Tratos joined industry experts at TOC-Europe
Round table on “Using innovation and standardization toward the decarbonisation of the transport sector”
Together with AENOR in protecting the environment
Tratos has made possible the first use of Bornewables™ in the energy industry
“Egidio Capaccini” Award - 2022 edition